If you are having problems logging in, please call HIA helpdesk on 1300 650 620 during business hours.
Enter details below and sign up
Although buildings constructed in bushfire-prone areas need to meet the requirements of building regulations and standards, it doesn’t mean that traditional building materials such as timber window and door frames are prohibited. On the contrary, a range of timber windows and doors have been bushfire tested to meet the radiant heat and flame exposure requirements of Australian Standard AS 1530 and are suitable for use in bushfire-prone areas.
A number of major window suppliers have a range of timber windows and doors that have been tested and satisfy the provisions of AS 1530.8.1 and meet the requirements for bushfire attack level up to BAL-40.
The Performance Requirement P2.7.5 of Volume Two (Class 1 and 10 Buildings) of the National Construction Code (NCC) requires a Class 1 building (including decks) or a Class 10a building that is constructed in a designated bushfire-prone area to be designed and constructed to reduce the risk of ignition from a bushfire, appropriate to:
The NCC defines a designated bushfire-prone area as land that has been designated under a power of legislation as being subject, or likely to be subject, to bushfires. As a consequence, the process for identifying bushfire-prone areas is a matter for each individual state and territory regulator. While it differs from state to state, it usually involves an approach to the relevant council or reference to a land mapping facility provided by the respective state regulator or agency.
Where an allotment is in a bushfire-prone area, the NCC goes on to provide building solutions that meet the requirements of P2.7.5. Part 3.10.5 provides three compliance options:
Following option 1 and using the Australian Standard approach, AS 3959 divides bushfire-prone areas into six bushfire attack levels (BAL) based on the severity of the building’s potential exposure to ember attack, radiant heat and direct flame contact:
AS 3959 covers the methodology for determining the BAL for an allotment and goes on to provide the construction requirements for each level of BAL, including for floors, roofs, external walls and windows, verandahs and carports.
By complying with the construction requirements for the respective BAL classification, a new home will meet the requirements of the NCC.
While the standard focuses on providing construction specifications for materials, elements of construction and systems for each of the six BALs, it also provides the alternative of using materials, elements of construction and systems that comply with the simulated fire testing provisions of Australian Standard AS 1530.8.1 (for BAL-12.5 to BAL-40) and AS 1530.8.2 (for BAL-FZ).
It is important to note that the Standard recognises more than one means of compliance. Although it recognises metal-framed windows and bushfire shutters, the Standard does not prohibit the use of traditional building materials such as timber windows and door frames (provided they have been fire tested and satisfy the requirements of AS 1530).
Clause 3.8 of AS 3959 prescribes that:
Where any material, element of construction or system satisfies the test criteria of either the relevant BAL construction requirements within sections 5 to 9 of AS 3959, as applicable of or the test criteria of AS 1530.8 series for BAL-12.5, BAL-19, BAL 29 and BAL-40 or AS 1530.8.2 for BAL-FZ, it satisfies the requirements of that BAL.
For example, in the case of BAL-40, the construction requirements are found in Clauses 8.2 to 8.8 of AS 3959.
While Clause 8.5.2 (a) of the Standard requires that windows are to be completely protected by a bushfire shutter complying with the Standard, Clause 8.5.2 (b) of the Standard also provides the alternative option of using metal frames and metal hardware, among other things (such as minimum 6mm thickness toughened glass).
Importantly, a third option of using a fire-tested system that has met the fire test requirements of AS 1530.8.1 is also available to designers, specifies and builders in BAL-40.
In particular, Clause 8.1 of AS 3959 describes that:
Any element of construction or system that satisfies the test criteria of AS 1530.8.1 may be used in lieu of the applicable requirements of Clauses 8.2 to 8.8 (see Clause 8.3).
Windows that meet the requirements of Clause 8.5.2(a) (using bushfire shutters) or 8.5.2(b) (using metal frames) or 8.1 (using windows that meet the simulated bushfire test criteria in AS 1530) will satisfy the requirements of the NCC.
Windows that meet the requirements of AS 1530.8.1 for a higher BAL than what is required for that building also meet the requirements for lower a BAL for example a window that is tested to BAL-40 also meet the requirements in BAL-12.5, BAL-19 and BAL-29.
It should also be noted that there are a number of state variations to the NCC and AS 3959 bushfire requirements, so it is always important to check the requirements in your state or territory.
More articles on:
Supporting building professionals with custom built services and products.
HIA TRADEPASS takes the hassle out of collecting and verifying contractor business information and registrations. Developed by HIA specifically to suit the needs of residential builders.